Norfolk, VA 23503
The customer called for an annual backflow preventer test. We arrived on site to test the 2 backflow preventers on the property and one passed but the other one had froze and split over the winter. We quoted the customer a price to replace the bad device. We returned on another day and replaced and tested the second device. The customer was relieved to have both of the backflow preventer working and passing the inspection.
- Robert Rollings
- Backflow Testing and Installation